Data Centers (NOC's)
At Beachcomber Creations we collocate our servers, the following description is from that data center information package. We are not attempting to imply that we own or have ownership in this data center, this page is simply for informational purposes for our customers so you can feel comfortable with the partners we choose and the location of your site and/or server.
Fortress ITX Data Center (New Jersey)
The FortressITX Data Center resides in Clifton, NJ, just 14 miles from New York City. This new facility boasts enormous growth potential allowing us capabilities of up to 55,000 sq ft of pure datacenter floor space, and ease of access to backbone providers. Currently, the facility incorporates over 7,500 sq ft of completed raised floor data center space, along with 4,500 sq ft of corporate office space which includes a front reception area, conference rooms, and ample space for our employees. The new datacenter has been carefully planned from inception to overcompensate for such factors as cooling, generators, UPS's, backup generators, fire suppression, and much, much more. Our new facility has been set in place with 7,500 sq ft of raised flooring, 4 (ten) 20 ton AC units and double pre-action fire suppression system. FortressITX currently uses MCI and Above.net as its backbone providers, and is adding Level3 and Global Crossing in the near future. FortressITX offers fast, reliable connectivity to the internet via an MCI OC48 Full Sonnet Ring with the addition of dual OC192's in the upcoming future.
GNAX Atlanta and Dallas Data Centers (NOC's) ;
GNAX's 75,000 square foot, SAS 70 Type II-certified data center in Atlanta, Georgia serves as its home base. Wholly owned and managed, the Atlanta facility serves as a staple to high-level, 24/7/365 security. With no single point of network failure, GNAX runs its own redundant metro Ethernet connections on a dark fiber footprint. Roof rights are available.
Multiple utility power feeds
Two 'A' feed (primary) UPSs | One 3-module (N+1) 750 kVA unit | One 4-module (N+1) 2000 kVA unit
One 'B' feed (redundant) UPS 1 module 750 kVA unit
Ten 500 kW diesel-powered generators (N+1 capacity), controlled by dual PSSI static switchgear units
On-site fuel storage tank
Redundant cooling towers
Multiple pumps (N+1) to circulate water to CRAC units
Multiple CRAC units setup in a zone configuration
36,000 gallon storage tank to hold make-up water for cooling towers
Private well to supply make-up water (well is backed up by city water)